The Model P-1 & P-2 Trap Primer Valve is a precision device designed to deliver potable water to floor drains.
A pressure drop of 10 PSIG (70 Kpa) is required to activate the priming valve.
The Trap Primer must be installed on cold fresh water lines of 1 1/2" diameter or less.
The valves operating range is 20 to 80 PSIG (138 to 552 kpa).
- Adjustable to line pressure
- Piston operated, contains no springs or diaphragms
- Easily adjusted to high or low pressures
Model P-1 will prime 1 to 4 floor drains using the PPP Patented distribution system
Model P-2 will prime 1 or 2 floor drains using the PPP Patented distribution system
|Construction:||Machined from C69300 ECO Corrosion Resistant Brass.|
|Piston:||Piston operated, contains no springs or diaphragms|
|Inlet:||1/2" NPT Male or
1/2" NPT Female or
|Pressure:||Easily adjusted to high or low pressures|
The priming valve must have a minimum elevation of 12 inches (305mm) above the finished floor.
Distribution Unit Installation:
Must Be Installed Level
Must Be Installed with Clear Plastic Cover
Must Be Installed with Access for Periodic Inspection
Do Not Subjetc Trap Primer Valve to Rough in Pressure Test
Please refer to the provided installation instructions when using our distribution units.
PART NUMBERS & SPECIFICATIONS
|PART NUMBER||# of Drains||Distribution Unit|
MULTIPLE DRAIN AND SINGLE DRAIN
Please contact us at 503-328-6705 for TECHNICAL/SALES Support.